Details about the VCR-X3M Interlock Lock
- Interlock locks are auxiliary devices designed to ensure that the doors of a room cannot be opened simultaneously, thereby ensuring isolation between clean and non-clean areas.
- The VCR-X3M interlock lock can control the opening and closing of three doors simultaneously.
- Specifically, if one door is opened, the remaining two doors will be forcibly closed, and if you want to open one door, it is necessary for the other two doors to close first.
- If someone attempts to open door number 2, a warning bell will sound to alert.
- In emergency situations such as power outage or fire, all three doors will be opened simultaneously to allow personnel inside to escape.
Applications of the VCR-X3M Interlock
- Installed in the control panel rooms of clean rooms, buffer rooms, airlocks, intermediate rooms, changing rooms using signaling systems in the medical field, laboratories, pharmaceutical manufacturing plants, electronics equipment, semiconductors, offices, and more.
- Used for entry doors, emergency exit doors, safety doors, etc.
Components of the VCR-X3M Interlock
- Control box
- Lock bolt
- Indicator light
Technical Specifications of the VCR-X3M Interlock
- Electronic interlock lock for three doors
- Control voltage: 12V
- Power supply: 220V; 50Hz
- Lock wire: 3M, length 4m / strand
- LED voltage: 5V
- Imported complete lock
- Warranty period: 12 months
Quality of the VCR-X3M Interlock
- Our product is widely used in the pharmaceutical industry and factories with clean rooms:
- Three-door interlock lock: Automatic system checks if all three doors are closed; if one door is not closed, it will send a continuous warning signal to remind users to close the two remaining doors.
- Product structure: It consists of three parts, including control equipment, electronic lock control, and electronic sensor switch.
- LED Display: The outer shell is made of plastic and equipped with LED display, making it visually clear and easy to operate.
- High Isolation: This interlock lock is specially designed for air isolation in clean rooms, often used in shock-reducing rooms or pneumatic valve rooms in clean rooms.
- Guaranteed Material: The material is meticulously chosen, with high stability and low power consumption. This system uses computer chip entry, high stability, high precision, compact size, and full functionality. The system’s power consumption is less than 12W, generates little heat, and has a longer lock lifespan, making it an ideal product for the clean industry.
Description of the Operation Process of the VCR-X3M Interlock
- When one door opens, the other two doors will automatically close, and all three doors cannot be opened simultaneously.
- If one door remains open for an extended period, a warning bell will ring to remind personnel to close the door.
- In case of a power outage and for electronic interlock locks, all three doors can be opened to ensure user safety.
- In case of an emergency, an emergency button can be pressed to forcibly open the doors.
Installation Diagram for the VCR-X3M Interlock
- The interlock lock control box will be installed on the ceiling panel, connected to an existing socket (the shorter the distance between the control box and the socket, the better, to save wiring costs).
- The indicator light will be mounted on the wall panel, in an easily observable area when entering/exiting, usually installed next to the panel door.
- The lock bolt will be installed underground inside the panel room (requires drilling and underground wiring), and it can be installed on the side or above the door frame.
- The lock bolt positioning plate will be attached to the door leaf, corresponding to the lock bolt installation area.
The VCR electronic interlock lock has gained trust from pharmaceutical factories nationwide, such as Hà Hưng Pharmaceutical, Hải Phòng Medical Supplies, Davina Factory, Amepro Pharmaceuticals, Đại Bắc Pharmaceuticals, Hoa Linh Pharmaceuticals, and the Accelerator Center – 108 Central Military Hospital.
Additionally, some important installation considerations for the interlock lock include:
- Securely connect the signal wires to the lock bolt and indicator light.
— > Error Warning: The alarm bell will sound loudly and continuously.
- Install the lock bolt and lock positioning plate in the same direction (Wi-Fi symbol) on both accessories.
— > Error Warning: The lock will not operate.
- Do not reverse the signal wires between the indicator light and lock bolt.
— > Error Warning: Unable to install. The signal wire of the lock bolt is usually slightly thicker than that of the indicator light, so please pay attention during installation.
- Use wire boxes and conduit to protect signal wires on the ceiling to prevent damage from insects. Signal wires are different from power wires, and if they are cut or damaged, they are difficult to reconnect.